The operation of the screw sludge dewatering equipment should first be followed by opening the cleaning valve on the equipment. After that, it is necessary to pay attention to the addition of the washing water. Ou Zhe is to clean the solvent for 30 minutes, and then reduce the rotation speed on the screw-type sludge dewatering equipment. The main machine frequency is 5-10HZ during cleaning, and the auxiliary machine can be stopped for cleaning 2-3 times. Each time it is rinsed for 15 minutes, if the accumulated material can not be washed clean, it should also pay attention to appropriate extended cleaning time. At the same time Care should also be taken to check if the feed valve is completely closed.
When using the screw sludge dewatering equipment, it should be careful to clean the drum spirally. This time to prevent the start of the sludge dewatering equipment again, because the material inside the machine is still destroying the balance or causing poor If the speeder parts are damaged, it is not allowed to leak materials into the machine after shutdown; Note: It is forbidden to pass the cleaning fluid after the dehydration equipment is shut down, so as to prevent the cleaning fluid from entering the main bearing and the spiral support bearing.
When the screw-type sludge dewatering equipment is in use, it should be noted that it is necessary to gradually reduce the amount of intake until it stops, and stop the dosing; after the main engine is stopped, it is also necessary to pay attention to pressing the red stop button; Our equipment is equipped with a protective circuit, and it is precisely because of this, when the host is running, it can open other auxiliary systems, in fact, refers to the dosing system and feed system.
The operation of the screw-type sludge dewatering equipment should be checked and the normal performance of the sludge dewatering equipment should be checked.
When screw-type sludge dewatering equipment is in operation, it is necessary to pay attention to detailed records of downtime, reasons and other necessary conditions; if the screw sludge dewatering equipment shuts down below 0°C in ambient temperature, it must also pay attention to make antifreeze. In other terms, this is actually to avoid the possibility of freezing inside the sludge dewatering equipment and damage to the screw and differential.